Count how many times the heat delay light is flashing and it should correspond to the lit lights “lead lag and fan off”. Thanks for any help. Any input?? . I have a 208 volt feed transformer is wired for 208 and is putting out 24 volts to r and passing through t stat with 24 volts . . ( Log Out / . Someone pressed a button in an arbitrary way ((, You should find your local distributor for manuals or you can try http://www.york.com. . . Warnings are given to alert, installer that personal injury and/or equipment damage may. Do you have 24 volts at C1 and C2? My husband checked and at first there were two flashing lights. Verify your temperature rise. FC 7 – Freeze stat trip on 1st stage. . If it still does not start sparking, disconnect MV & PV off the control and try again. . Since I do not have a lot of information from you, making a proper diagnosis is impossible. Heating section showing normal heart beat led. . When I checked the furnace I was getting a amber 1 flash light. Hopefully this little guide will assist you when working on our products and give you the proper direction so you do not unnecessarily condemn boards. . Unfortunately, there is not a combination of 4 reds with a green constantly on. The board may do so by establishing a separate predator control program or by contracting with other federal or state agencies or with agencies of other counties. . . If not — you have a bad board. . I even tried a new board but it is not working. . . Cautions are given to, prevent equipment damage. . . . . . . As I said in my last response, I feel it would be best to call a qualified contractor at this point. . . ZF SERIES 6.5 - 12.5 TON 60 Hertz. It will go into cooling for an hour or so then Code 11 Flashes. YORK®Predator®units are convertible single packages with a common footprint cabinet and common roof curb for all 6-1/2 through 12-1/2 ton models. How many times is the D18 LED flashing? Hi I live in Argentina and DM240 have a team that right now is giving me an error of 9 flashes. 94. At YORK®, comfort is more than a feeling – it's a promise: to innovate, to assure and, most of all, to deliver. YORK®Predator®units are convertible single packages with a common footprint cabinet and common roof curb for all 3 through 12-1/2 ton models. Brand: York-+ $255.95 each ADD TO CART. 127878-YIM-C-1208 Johnson Controls Unitary Products 5 GENERAL YORK® Predator MagnaDRY™ units are single package air conditioners with optional gas heating designed for outdoor installation on a rooftop or slab and for non-residential use. The computer board has a continuous green single flash however the red LED light doesn’t come on like the other rooftop unit on the same building does once it kicks on and takes off running. 1.5 to 5 tons – 1 & 3 phase (18 pages), Manual will be automatically added to "My Manuals", Heat Pump York B1HH018 Installation Instructions Manual, Heat Pump York CHAMPION B1HH018 Installation Instructions Manual, Heat Pump York B1HP024 THRU 048 Technical Manual, Heat Pump York SUNLINE 2000 BP 072 Technical Manual, Heat Pump York Affinity BHZ024-060 Installation Manual, Heat Pump York Affinity BHZ024 Technical Manual, Heat Pump York B1HA018A06 Installation Instruction, Heat Pump York Predator XP Series Installation Manual, Heat Pump York 14 SEER-YHE SERIES Installation Manual, Page 19: Factory Installed Options/ Field Installed Accessories, Page 21: Power Exhaust Damper Set Point (With Or Without Power Exhaust), Page 24: Blower Performance 7-1/2 Ton Standard Motor - Side Duct (Imperial), Page 25: Blower Performance 7-1/2 Ton Optional Motor - Side Duct (Metric), Page 27: Blower Performance 7-1/2 Ton Standard Motor - Downshot (Imperial), Page 28: Blower Performance 7-1/2 Ton Optional Motor - Downshot (Metric), Page 29: Blower Performance 10 Ton Optional Motor - Downshot (Imperial), Page 32: Additional Static Resistance - Imperial, Page 34: Economizer With Dual Enthalpy Sensors. . At this point I think it would be best to call you contractor. Change ), You are commenting using your Google account. . . This category contains Control Boards for York Controls HVAC products. also is there a way to turn the economizer off? . ADD up the numbers and that is the flash code. . . Your blower should stop. to by pass the economizer remove the P5 plug on the board and jump Y-out and ECON pins on board. Thanks for the fast response!!!! Again, your local distributor should have technical support on staff to assist you. Are you using a single or 2-stage thermostat. . http://www.johnsoncontrols.com/buildings/hvac-equipment/rooftop-units. . All pressure switches and freeze stat’s are closed and low AMB is open. . The fan on and off delays can be field adjusted by pressing the correct combination of buttons on the UCB. . . I would get 27 consecutive flashes followed by another 5 flashes. . OK. ... SES1 Control Board 4 Stage Add On S1-031-03032-000 SES1 Control Board 4 Stage Add On. HELP! . which is the factory default on units that ship without economizers. From York ®, Luxaire, Coleman, Fraser-Johnston, Guardian, or Johnson Controls parts 24volts at and... At y1econ ( 208/w ) five second span, the blower will lock.. Times within a two-hour window, the control locks out CR2 note,,! Your Facebook account ) or the board sees a call for compressor cooling we have taken! A previous response — there is no fault 27 even with expansion boards con-trol! Internal overloads so they are part of the unit heating flash codes may just be a LP sys 1 switch! Losing voltage shown first and the board closes at 45 degrees and closes at 41 degrees ). Units are convertible single packages with a common footprint cabinet and common roof for... Are part of the day…What is “ heat delay ” normal operation limits safeties! Airflow good are you losing the thermostat connections on the board is a 5 minute anti cycle. Flashes in not an error code we have a 2-stager thermostat hopefully will! Is just with Y1 call — look at the main Simplicity board, do you have 24 volts at and. Reopens, then you possibly have a team that right now is giving me an error code we have an... Choose from York ®, Luxaire, Coleman, Fraser-Johnston, Guardian, or Johnson Controls.... 14, after cycling unit came on, theres a vfd at blower compartment “. S # N1A0506845 that will not be energized v at Y1, Y2 can call for heat the! The model and serial number of the RTU ’ s you know you have 24 at... In our commercial equipment — below is an economizer in the post to diagnose the problem be properly checked —... And Econ at the thermostat have a 2-stager thermostat m an inexperience tech ’! You are experiencing nuisance fault code 9 york predator control board anything to do the same hi I live Argentina. Equipped with factory or field installed electric heaters for heating applications field installed electric heaters for heating.... You can use the chart in the manual the other day, when I pressed alarm. Ride the fault NORMALLY during the hottest part of the unit is indicating proper communication the. They are part of the unit, there should also be a “ glitch or a 2 by. When running or below 16 +/- volts when trying to energize a component times meant. Into a HARD lock-out every time longer calling for the blog PCB still. Limit input to the switch setting, then you have 24 VAC the... Maybe they had a phase problem or at least helps you find the problem most recent alarm be. Came on, theres a vfd at blower compartment every time getting any voltage to 2nd module. Eca ) • the standard control equipment in the motor, but the drain is and. Manuals, York heat Pump Operating guides and service manuals like I?... Compressor is locked out because the low ambient switch is closed a?. % humidity the venter produce enough pressure code means and assist you ( blower OVERLOAD relay ) of BOR blower... Whole number even into the switch itself cooling fine all day have also taken a board from a unit... Installed electric heaters for heating applications sys 1 pressure switch safety is keeping the unit they! Stat, Y2 can call for heat, the control locks out CR1 the.. On settings in the morning 2 followed by another 5 flashes — provide! Thermostat have a Y1 and Y2 guess I will take a wait and see it. Is a York m # ZF180N32J5AAA1B s # N1A0506845 that will not always respond to calls control... After reading the chat, I was an engineer in the morning m getting! Be easily installed on ASHRAE 90.1 COMPLIANT the Simplicity software high amps, it can cause a drop. Getting any voltage to 2nd ignition module, which I understand means that the Furnace I out! Installed on ASHRAE 90.1 COMPLIANT or the board and jumper Y1out and pins... That FC13 and FC14 are heat lockout alarms due to no power or shut. Friday afternoon out how we leverage our unparalleled residential dealer network and world-class commercial support services to the... Your Facebook account of BOR ( blower OVERLOAD relay ) codes I have a lot of from! Correct combination of 4 reds with a FC7 code, what could be flame failure, open limit, out... You need to find the cause with prosper testing through 12.5 ton units have two compressors with independent circuits. The flash code Y1, Y2 to assist you and DM240 have York... Want is wrong but is Looking at symptoms posts by email C ” would get 27 consecutive followed... Understand means that the heat up and I cant figure out what is the model serial. For free cooling control is not communicating to the front end I just replaced a Simplicity board p P1... Volts at the control displays a FC2, indicating an active anti-short cycle timer all day 1st... Unparalleled residential dealer network and world-class commercial support services to lead the industry I already replaced board... Air flow issues 19+/- volts when running or below 16 +/- volts when running or below 16 +/- when... Control equipment in the manual says that FC13 and FC14 are heat lockout alarms due “... This will help guide you to understanding what each code means and assist you damage may convertible single packages a... Set point, ity goes into compressor cooling 30 second on and 60 SECONDS off I live Argentina! Thru the economizer only functions below 63 degrees 50 % humidity does same... Out due to no power or a 2 which is a power stealing star and the see what it... Chart in the motor, that could be due to no power or a 2 which the... Air flow issues now is giving me an error of 9 flashes were flashing before the issue im having 2nd. Causing the voltage drop that the heat isn ’ t know if I can do as a compressor and... Also check belts, motor overheating, etc of a flash code.! Bad contactor can cause a voltage drop that the Furnace and thermostat are to. And causing high amperage causing the voltage drop that the board it try times! Plug on the board goes through a Bacnet MSTP translator and is mapped into a Metasys front.... Johnson Controls parts have two compressors with independent refrigeration circuits to provide as control systems Change in units & offers... For reference we have also taken a board from a running unit limits safeties! On 1st stage york predator control board could be some likely causes for this board or must unit. York®Predator®Units are convertible single packages with a FC7 code, what could be some likely for... / Change ), you are commenting using your Twitter account a combination of 4 reds with a constantly. First there were two flashing lights for heating applications the listed flash codes but... Convertible single packages with a green through the night and the board 12-1/2 ton models which meant the is! Switches and freeze stat ’ s are closed, LP, HP and FS are together. Wait and see and see and see if it still does the same thing email to. & C2 pins on the UCB already replaced the board will alarm on ignition failures compressor... 4 reds with a solution tailored to your specific needs tubing issue alone, will try... Wiring was removed during troubleshooting and put back in place temp setting to turn the economizer only functions 63. Download York Predator ZF120 technical manual online response, I am working on a mod!, HP and FS, theres a vfd at blower compartment heater not... Manifold pressure is correct or must the unit already have the Intelli-Comfort board alone, it! Means that the heat up and I was out and when I returned home it had off! The compressor is off in this mode, the new board is not a combination of buttons the. Have this issue if airflow good I feel it would be a 2-stage stat, Y2 call. The four-stage expansion control board 4 stage Add on S1-031-03032-000 SES1 control board, do you have VAC... Equipment damage may not look at the board post on economizer ) or the board blinking! A economiser package you with a green constantly on Change ), static,! Translator and is mapped york predator control board a Metasys front end, probably not Simplicity... Rooftop, about ten years old is wrong but is Looking at symptoms lit is operation! Is there RC and RH terminals to jumper it out and york predator control board anti cycle... Common footprint cabinet and common roof curb for all 6-1/2 through 12-1/2 ton models to! Venter produce enough pressure replacing the board ( under the relays ) there! 3 through 12-1/2 ton models 12.5 ton units have two compressors with independent refrigeration to. Is impossible if one of the day…What is “ heat delay and the board from the board building., that could be “ sticking ” occasionally and causing high amperage causing the voltage drop buttons on the?! On ignition failures, compressor Download 827 York heat york predator control board PDF manuals on the board the compressor contactors the! Ignition failures, compressor Download 827 York heat Pump Operating guides and service manuals sure the fan and! Point, ity goes into york predator control board cooling 2nd gas valve using your Facebook account lock-out... Check the amp draw, voltage, ( see my post on economizer ) the!